Відгуки відвідувачів - Написати рецензію
Не знайдено жодних рецензій.
Інші видання - Показати все
Add to Sec alternating currents amperes appliances approved arc lamps arc light armature automatic belt bidder brackets building candle power ceiling centre of distribution conductors conduit connected contractor shall furnish cord covered cross-arms cut-out boxes cut-outs and switches device direct currents distance distribution circuits double pole double-pole cut-out ductors dynamo electric light engines exterior feeders fixture schedule floor full load fuses gas pipes globe ground incandescent lamps inclosed incombustible bases Inside Wiring installation insulated joints junction boxes least less lightning arrester low poten Low Potential lowering lamps mast-arms material mechanical injury metal meter moisture moisture-proof necessary non-combustible non-inflammable Note.—Specify Note.—The specification number of lights operation pendants placed plant pole line porcelain pressure wires protected pulleys raising and lowering regulator riser safety fuses secure sockets soldered spark arresters steam switchboard three-wire tial system tion total number tube two-wire volts walls wirp
Сторінка 110 - Must be so placed in wet places that an air space will be left between conductors and pipes in crossing, and the former must be run in such a way that they cannot come in contact with the pipe accidentally. Wires should be run over, rather than under, pipes upon which moisture is likely to gather or which, by leaking, might cause trouble on a circuit.
Сторінка 105 - Must be so spliced or joined as to be both mechanically and electrically secure without solder. The joints must then be soldered, to insure preservation, and covered with an insulation equal to that on the conductors.
Сторінка 116 - Must be so suspended that the entire weight of the socket and lamp will be borne by knots under the bushing in the socket, and above the point where the cord comes through the ceiling block or rosette, in order that the strain may be taken from the joints and binding screws.
Сторінка 120 - Must be capable of being disconnected at the power plant, or of being divided into sections, so that in case of fire on the railway route, the current may be shut off from the particular section and not interfere with the work of the firemen. This rule also applies to feeders.
Сторінка 114 - ... b. Must always be placed in dry, accessible places, and be grouped as far as possible. Knife switches must be so placed that gravity will tend to open : rather than close the switch.
Сторінка 105 - Must be so placed that moisture cannot form a cross connection between them, not less than a foot apart, and not in contact with any substance other than their insulating supports.
Сторінка 111 - The object of a tube or conduit is to facilitate the insertion or extraction of the conductors to protect them from mechanical injury and, as far as possible, from moisture.
Сторінка 115 - No combination fixture in which the conductors are concealed in a space less than one-fourth inch between the inside pipe and the outside casing will be approved. h. Each fixture must be tested for "contacts...