Відгуки відвідувачів - Написати рецензію
Не знайдено жодних рецензій.
Інші видання - Показати все
Alternating Current ampere meter apparatus appliances approved arc lamps arc light armature attached automatic belt building c. p. lamps candle power ceiling centre of distribution cleats concealed conductors conduit connections contractor shall furnish covered cross-arms cuits cut-out boxes cut-outs and switches device Direct Current distribution circuits double pole double-pole dynamo efficient electric light electromotive force engines exciter fastened feeders fixture floor foundation(s full load fuses fusible gas pipes globe ground heating incandescent lamps inches inclosed incombustible bases insure joints junction boxes least lightning arresters Low Potential main wires material mechanical injury metal moisture-proof molding necessary non-combustible non-inflammable number of lights number or designation ohms operation outlets pendants placed porcelain possible proper protected pulleys Rating ratus riser rules safety fuse securely separated shunt socket soldered spark arresters specification steam supported switchboard three-wire tion Trade number tube two-wire voltmeter volts walls waterproof insulation
Сторінка 131 - It must be clearly understood that the size of the fuse depends upon the size of the smallest conductor it protects, and not upon the amount of current to be used on the circuit. Below is a table showing the...
Сторінка 122 - Must be so spliced or joined as to be both mechanically and electrically secure without solder. The joints must then be soldered, to insure preservation, and covered with an insulation equal to that on the conductors.
Сторінка 134 - Must be so suspended that the entire weight of the socket and lamp will be borne by knots under the bushing in the socket, and above the point where the cord comes through the ceiling block or rosette, in order that the strain may be taken from the joints and binding screws.
Сторінка 138 - Must be capable of being disconnected at the power plant, or of being divided into sections, so that in case of fire on the railway route, the current may be shut off from the particular section and not interfere with the work of the firemen. This rule also applies to feeders.
Сторінка 134 - The wires used with the fixtures must have a non-inflammable insulation, or, where concealed between the pipe and shell of the fixture, the insulation must be such as required for fixture wiring for the electric light. c. The whole installation must test free from "grounds.
Сторінка 132 - MOTORS — a. Must be wired under the same precautions as with a current of same volume and potential for lighting. The motor and resistance box must be protected by a double-pole cut-out and controlled by a double-pole switch, except in cases where one-quarter horse-power or less is used. The...
Сторінка 122 - Must be so placed that moisture cannot form a cross connection between them, not less than a foot apart, and not in contact with any substance other than their insulating supports.
Сторінка 129 - The object of a tube or conduit is to facilitate the insertion or extraction of the conductors to protect them from mechanical injury and, as far as possible, from moisture.