« НазадПродовжити »
(See Note: p. 46, sec. 22.) 34The foundation(s) for the(se) dynamo(s)
shall be built by the
laid , or of other material subject to
the approval of the j JggES. [ andsha11 be of sufficient length, width, and depth
to safely and firmly sustain j \^>1T ^
weight. The foundation(s) shall be capped with a framing of well-seasoned timber securely fastened thereto, the dynamo baseframe(s) being securely fastened to the framing or to the foundation through the framing, both framing and baseframe being secured in such a manner as to prevent lateral motion in either direction and to give an even bearing surface at every point. If metal is used to fasten framing or baseframe to the foundation it must be thoroughly insulated where it passes through them, and at all places liable to come in contact with the dynamo must be countersunk and covered with a moisture-proof insulating compound.
All necessary excavating and filling and the removal of all debris shall be
done by the [who shall also
restore the floor in the following manner: . The height of the dynamo baseframe(s) above the floor line will be .
35. instru- (See Note: p. 48, sec. 23.)
There shall be provided with each dynamo one voltmeter or pressure indicator which shall remain constantly in circuit so as to indicate at all times the pressure at the point to which it is connected; one brush jig for trimming the brushes; one insulating baseframe provided with rails and a suitable device for shifting the position of the dynamo to alter the belt tension; if of the constant-potential type, one hand regulator made entirely of incombustible material, a compensator or suitable balancing device for keeping the current in each circuit practically constant; if of the constant-current type a regulator for so controlling the potential as lights are turned on or off that the current shall not vary appreciably from its normal value under any condition of load. There shall be provided for each circuit one ampere meter for indicating the current in said circuit, one ground detector which shall continuously indicate the insulation from the ground maintained at both poles and approximately the distance of any ground from the station, and one pair of lighting arresters. There shall also be provided one testing set capable of measuring up to ohms.
This contractor shall carry to the ^
switchboard location at all regulator,
exciter, auxiliary and main wires, leaving the ends, coiled up neatly, properly tagged and sufficiently long to make the necessary switchboard connections. All main wires shall have a capacity of at
least C. M. per ampere and no wire
smaller than B. & S. or B. W.
G. shall be used. All wires shall be in
sulated with ;shall be run ;when
of opposite polarity shall be separated at
least ;and where crossing each other,
wires of other circuits, or passing near metal pipes, girders, etc., shall be further protected by . In no case shall insulated wires be carried in such proximity to heated surfaces, vapors or air as to endanger their insulation.
(Seep. 51, sec. 25.)
38. Renewal (See p. 51, sec. 26.)
39. summary. (gee Note: p. 52, sec. 27.)
Each bidder shall fill out completely the following summary:
Number of dynamos
Trade number or designation .
Rating in volts
Rating in amperes
Direct or alternating current . .
Constant or varying current . .
Constant or varying potential . .
Series, shunt, compound, self or
Rating of exciter in volts . . .
Rating of exciter in amperes . .
Trade number or designation . . —
Regulation by hand or automatic
Number of fully loaded circuits pos-
Volts per c. p. lamp . . . —-—
Amperes per c. p. lamp . .
H. P. required to be delivered at
the pulley at full load . . .
(See p. 53, sec. 28.) 40. ^witch
There shall be placed upon this switch- «• switchboard Appa
board, in addition to all the dynamo regu- confections, lating apparatus, such switches, cut-outs and other appliances as are necessary for the proper and convenient manipulation of the circuits, such appliances to be named by each bidder in his proposal. For systems operating dynamos and circuits in parallel, the appliances and connections shall be such as will permit adding to or taking from the circuit any