« НазадПродовжити »
and on the plans, meter outlets shall be run (and a support for each meter provided consisting of — securely fastened to the wall).
Each elevator is to be provided with 99.Lieberator
-,- c. p. lamp(s). Each elevator shall be on its own cut-out and circuit which shall be run from the distribution box at (location). The wiring shall include the wiring of the elevator car, all necessary cables and the connection with its outlet. The cables shall be well insulated, flexible and properly protected from abrasion.
The molding used in the places speci- 100. Molding. fied above shall be of — , and finished
On all outside walls, bare brick or stone walls, etc., it shall consist of a backing and capping.
While the schedule is intended to rep- 101. Additions resent very closely the number of lights
and outlets to be wired to, yet, as some changes may become necessary during the process of construction, each bidder shall name in his proposal a price to be added to or deducted from the contract price for each light or outlet wired for in excess of the number specified, or which shall be cancelled, provided such addition or cancellation involves no change in the work already completed and shall be along the lines of existing circuits.
102. Instruc- (Note. It may be desirable that the
purchaser furnish one man to work under the contractor in order that he may have a man thoroughly familiar with all the details of the construction; the contractor to give such instruction as will enable him to acquire a thorough and intelligent knowledge of methods, appliances, location of circuits, etc.)
103: Hanging (Note.-To be inserted if this contract
or is to complete the wiring, including the attachment of lamps and sockets.)
This contractor shall hang all fixtures, including the assembling and wiring of the fixtures (unless provided for under Fixtures), the attaching of sockets, lamps and shades, and the connection with the ends of the taps.
Insulating joints will be furnished, where required, by the fixture contractor but this contractor shall furnish and connect a suitable cut-out for each outlet, protecting both sides of the circuit.
04. Wiring This contractor shall attach- sockets 104.
m omenti ing Sockets by means of a (suitable gas attachment) to Fixtures
already in to the (gas) fixtures already in place. These fixtures shall be properly insulated and shall be wired in the following manner: — — with — At each outlet a suitable cut-out shall be provided protecting both sides of the circuit. In each socket the proper lamp shall be placed and all shades shall be attached.
Sockets and lamps shall be suspended 105. Suspen.
sion of Sockets by means of — pendants from the ceil- and
ing. Each pendant to be — in length, (provided with a cord adjuster) and protected by a double-pole ceiling cut-out. Both at the cut-out and in the socket the cord shall be knotted so that in no case will the weight come on the binding screws. Where the cord passes through the neck of the socket it shall be protected by a — bushing. In each socket the proper lamp shall be placed and all shades shall be attached.
This specification is identical with the two-wire specification, except in “System,” p. 94, sec. 84, in place of which insert the following:
Aurisers ļ and mains shall be fig. 106. System.
17 feeders an ured on the basis of the three-wire system, but the distribution circuits shall consist of two wires only except to outlets for a group of — , - c. p., lamps or more, and for special circuits specifically mentioned. Care shall be taken in arranging the distribution circuits to have the same number of lamps on each side of the system and that no circuit shall be connected across the outside wires. The neutral wire shall in all cases be properly tagged and shall be run between the outside wires.